Your Glen Burnie Plumber
Do you have a higher utility bill this month? Your plumbing may be the problem. Contact your local Glen Burnie plumbing experts at Heidler, Inc. We are ready to solve your toughest problems. Call (410) 268-7191 for flat-rate service and quality solutions. Click here to view our current specials discounts.
To see what your neighbors are saying, click here to read our latest customer reviews.
What are signs your sewer line needs repair?
Is sewer waste leaking onto your lawn? This is an emergency that requires immediate attention. Contact us for an inspection and the most cost-effective method of repair.
There are several signs that point to sewer line problems:
- Gurgling sounds coming from the toilet
- Sewer water puddling in your yard
- Slow-draining sinks, showers, or tubs
- Sewer backing up from your kitchen or bath drains
If you notice any of these problems, give us a call for immediate service.
Do you need professional drain cleaning services?
Drain clogs are common plumbing problems. Many homeowners try to solve minor clogs with a plunger or chemical drain cleaner. However, you cannot get rid of a severe clog unless you remove it completely from your sewer or drain line.
Common signs you need professional drain cleaning:
- Water is slow to drain
- Drains are producing a foul odor
- Water starts to back up from your drains
Is your water heater failing?
Don't let a failing water heater keep you from the hot water you need. Call your water heater experts at Heidler, Inc. to repair or replace your unit.
We recommend replacing your water heater if it has been in use for over 10 years, and is frequently breaking down.
Other signs that it's time to replace your water heater include corrosion or rust in the tank. If your water heater fails to maintain a consistent temperature, it may be time to replace it as well.
We will help you choose the right water heater to match your needs while staying within your budget.
Ran new 1/2 trac pipe from basement to new range location connected to main and stove. Installed stove
Found leak coming from 1/2 copper pipe pinhole on pipe feeding Unit# 303. I made temp repair. Need to return to shut down building and make repairs.
Replaced main s/o with new ball valve also replaced service stops and cartridges in lav faucet in ball bath
Replaced sewer service line.
Investigated sump pump not working properly, found foundation leak, referred to mason.
Inspected A.O. Smith gas water heater, ordered pilot assembly and gas valve to repair under manufacturer warranty.
Investigated gas pressure issues with fireplace shutting off when other gas appliances are running.
Founds 2" galvanized drain piping basement leaking. Replaced leaking section with 2" pvc. Also snaked from basement clean out for laundry and kitchen. 24 ft to clear stoppage.
Opened a small section of ceiling in 104's bathroom. Tested and checked all plumbing above unit 204. Found leak coming from shower/tub. Maintenance is aware and will go out tomorrow to address the situation.
Ran unit for 40 min. Everything looks good. Can't see a reason unit would shut off. Possible down draft blew out pilot.
Work with the plumbers who will treat your home with respect. Heidler, Inc. tailors every service call to your specific needs, so you receive a comprehensive solution that provides long term benefits. Call us today at (410) 268-7191 for upfront rates. You will know what to expect before any work begins.